发布日期：2016-07-27 作者：地源热泵公司 点击：
Speaking of GSHP, believe that there are a lot of people are not unfamiliar, the system mainly includes two parts, one is the water loop air conditioning system in the building, two is the underground part of the ground source heat pump air-conditioning system, the next Xiaobian and we discuss how to deal with the underground water source heat pump system in the.
When the sand content of the groundwater is high, the filter or the sand removal equipment should be used for treatment. At present, the widespread use of small volume, high efficiency, sand removal can remove water sand in the uninterrupted supply of water under the condition of cyclone desander. According to the processing flow of the type and number of optional desander. Some of the larger water turbidity, recharge and aquifer wells easy to cause filter clogging, affect the stability and service life of the water supply system. For water with large turbidity, a water purifier can be installed to filter the water.
Some water sources are highly mineralized and strong corrosiveness to metals. Directly entering the unit will reduce the service life of the unit. If the water treatment is used to reduce the salinity, the cost will be great. The iron content in the groundwater in our country generally exceeds the allowable value, so iron removal is necessary before use. The anti scale device of ion rod is a new advanced water treatment equipment. It has the functions of anti scaling, descaling, rust removal and corrosion prevention, with small power consumption and long service life.
The above is the knowledge that Xiao Bian tells you. We have strict working attitude and skilled working skills. We will ensure that tasks are done accurately and efficiently.