发布日期：2018-04-09 作者：地源热泵 点击：
1. The floor heating system should be cleaned once a year before use. Specific methods are as follows: firstly, in close connection pipe backwater valve, then open the filter, remove the filter and clean, check the filter is damaged and blocked, if damaged, should be replaced with the specifications of the filter, as it can be installed.
2, low temperature hot water floor radiant heating system water temperature should not exceed 60 degrees, the heating system work pressure shall not exceed 0.8MPa.
3. The water flow of each branch of the system can be adjusted by adjusting the ball valve on each branch, so as to control the temperature of each part, but should be adjusted carefully so as not to influence the other branches.
4, the ground heating system in the beginning of water supply or use process, the pipe may accumulate air, affect the heating effect, at this time, you can open the water bleeder valve, exhaust the gas, the method is the same as the traditional heating.
5, users really need to drill holes in the roof, we must pay attention to drilling depth can not exceed the thickness of the floor structure, in order to prevent damage to the ground floor heating pipe.
We will use good, appropriate service, so that customers feel the warmth of family ties, always depending on the safety of customers, such as ourselves. We will use our natural advantage to create a unique product that will give consumers a unique mood to enjoy the product.